|Place of Origin:||China|
|Minimum Order Quantity:||100SQM|
|Packaging Details:||28pcs/box ,32-36box/pallets,13pallests/20GP|
|Delivery Time:||7-10 work days|
|Payment Terms:||L/C, D/A, D/P, T/T|
|Supply Ability:||1000000 Square Meter/Square Meters per Month|
|Product Name:||Anti Static PVC Flooring 600*600mm / 590*590mm / 610*610mm With 3mm Thickness||OEM:||Available|
|Size:||600*600mm,590*590mm,610*610mm||Place Of Origin:||Jiangsu, China|
anti static flooring,
conductive vinyl flooring
Static electricity swoon everywhere in our daily life,there might be super high static electricity voltage around us or surrounded the body,thousands of volts or even ten thousands of volts.35,000 volts of static electricity generates when walking pass the chemical fiber carpet,about 7000 volts when reading plastic manuals,which might bot be felt by people,however it's fatal hazards to some sensitive equipments.Static electricity hazards may cause very serious consequences and losses.It could inadvertently shoot expensive devices,resulting in billions of dollars losses in electronics industry annually……
Nowadays people increasingly realize the importance and necessity of ESD protection,while the anti-static PVC floor system is the top priority of electrostatic protection.Perfet anti-static PVC floor system could prevent static electricity from generation,release static electricity into the earth to prevent accumulation of dust.
Anti-static PVC floor has been widely applied to e-shop,clean rooms,communication rooms and other precision instruments and rooms for equipment operation.
|Technical Data||Test Method||Test Results|
|1||Size||EN426||600 x 600mm, 900 x 900mm|
|3||Weight||EN430||3.8kg / 5.7kg|
|DIN51953 ASTM F-150 OR NFPA99||Antistatic Tile: 10^6~10^9 ohm|
|5||Conductive Tile: 10^4~10^6 ohm|
|9||Combustion Properties||SJ/T11236-2001(<10S,reach FV-0)||0.35IFV-0|
|10||Amount of Anti Wear||SJ/T11236-2001(≤0.020g/cm 21000r)||<0.014|
|11||Anti Wear Properties||EN660pt2||ITEN-T<2.0mm3|
|12||Wheel Pressure||EN425||No influence|
Brief Introduction of Installation
(1)the requirements of foundation
1.The ground should be waterstone ground, ceramic tile ground, wooden ground or cement ground.
2.The ground should be smooth and level. Its unflatness should be less than 0.2%.
3.The ground should have enough strength and no the phenomenon of sand coming out and separation.
4.The ground should be dry. It is necessary for a new ground to dry about 30days
(2)Procedure of construction
Clean the ground - spread the earthing conductive net-lead out the earthing line-coat strong adhesive-coat conductive adhesive-lay floor-welding floor-cleaning-inspect properties
(3)Maintenance of floor
1.It is not permitted that sharp and rough heavy matters scribe and drag on the surface of floor and that personnel who wear shoes with nails walk on the floor. The floor should be kept cleaning.
2.It is not permitted that the chairs which have black rubber cushion put on the floor in order to avoid black sulfide polluting its surface.
3.If there are oil or dirty on its surface, it may be cleaned with detergent. If there is scribed sign, if can be recovered through fine abrasive paper.
4.If there are heavy oil and dirty caused by install equipments. Our factory has special washer to clean them.
5.Our factory also has anti-static wax that can be used to maintain the floor. In general, it should be coated one time every six months. If the personnel walking on the floor are busy, it should it should be coated every three months.